test code for step-voltage regulators. IEC , Insulated bushings for alternating voltages above 1 V. IEC , Tap-changers – Part 2. This part of IEC is intended to assist in the selection of tap-changers designed in accordance with IEC or IEEE Std. C for use in. Tap-changers –. Part 2: Application guide. Reference number. IEC (E). This is a free 6 page sample. Access the full version online.
|Published (Last):||19 June 2016|
|PDF File Size:||1.78 Mb|
|ePub File Size:||12.8 Mb|
|Price:||Free* [*Free Regsitration Required]|
Thyristor-assisted tap changers use thyristors to take the on load current while the main contacts change over from one tap to the next. Agbioeletric Balun Buchholz relay Bushing Center tap Circle diagram Condition monitoring of transformers Copper loss Dissolved gas analysis Electrical insulation paper Growler High-leg delta Induction regulator Leakage inductance Magnet wire Metadyne Open-circuit test Polarity Polychlorinated biphenyl Quadrature booster Resolver Resonant inductive coupling Severity factor Short-circuit test Stacking factor Synchro Tap changer Toroidal inductors and transformers Transformer oil Transformer oil testing Transformer utilization factor Vector group.
It is designed to cover every economic sector and virtually every activity of the humankind where technical standards may be used. Also called On Circuit Tap Changerin applications where a supply interruption during a tap change is unacceptable, the transformer is often fitted with a more expensive and complex on load tap changing mechanism.
Also assists in understanding the various types of tap-changers and their associated equipment available. Retrieved from ” https: In other projects Wikimedia Commons. Amorphous metal transformer Austin transformer Autotransformer Buck—boost transformer Capacitor voltage transformer Iev transformer Delta-wye transformer Energy efficient transformer Flyback transformer 60214- transformer Instrument transformer Current transformer Potential transformer Isolation transformer Linear variable differential transformer Pad-mounted transformer Parametric transformer Planar transformers Rotary transformer Rotary variable differential transformer Scott-T transformer Solid-state transformer Trigger transformer Variable-frequency transformer Zigzag transformer.
Wikimedia Commons has media related to Tap changers. The tap selection on any tap changer may be made via an automatic system, as is often the case for OLTC, or a manual tap changer, which is more common for NLTC.
September Learn how and when to remove this template ice. The result operates like a dual-clutch transmissionwith the tap selector switches taking the place of the gearbox and the diverter switch taking the place 60214- the clutch.
Automatic tap changers can be placed on a lower or higher voltage winding, but for high-power generation and transmission applications, automatic tap changers are often placed on the higher voltage lower current transformer winding for easy access and to minimize the 6214-2 load during operation.
A reactance type tap changer uses a dedicated preventive autotransformer winding to function as the diverter impedance, and a reactance type tap changer is usually designed to sustain off-tap loading indefinitely. If only one tap changer is required, manually operated tap points are usually made on the high voltage primary or lower current winding of the transformer to minimize the current handling requirements of the contacts. Views Read Edit View history.
The disadvantage is that all 602144-2 thyristors connected to the unselected 62014-2 still dissipate power due to their leakage currents and they have limited short circuit tolerance.
In moving to tap 3, the following sequence jec. To minimize the number of winding taps and thus reduce the physical size of a tap changing transformer, a ‘reversing’ tap changer winding may be used, which is a portion of the main winding 6021-42 to be connected in its opposite direction buck and thus oppose the voltage.
Although we endeavour to maintain an up-to-date catalogue, on occasion we may not have the latest version of a document, including where it has not yet been provided through an international feed.
They are often more costly but this method is used in some modern transformers. To prevent contamination of the tank oil and facilitate maintenance operations, the diverter switch usually operates in a separate compartment from the main transformer tank, and often the tap selector switches will be located in the compartment as well.
Diverter resistor A is short-circuited; diverter B kec unused. Siemens — via http: Transformers with this mechanism obtain this variable turn ratio by connecting to a number of access points known as taps along either the primary or secondary winding. Some 6021-42 is unavoidable, and both the tap changer oil and the switch contacts will slowly deteriorate with use. This article includes a ice of referencesbut its sources remain unclear because it has insufficient inline citations.
Articles lacking in-text citations from September All articles lacking in-text citations Commons category link is iwc Wikidata. Covers both on-load tap-changers and off-circuit tap-changers. However, a transformer may include a tap changer on each winding if there are advantages to do so.
On load tap changers may be generally classified as either mechanical, electronically assisted, or fully electronic.
A tap changer ief a mechanism in transformers which allows for variable turn ratios to be selected in discrete steps. No load tap changers are 600214-2 employed in high voltage distribution-type transformers in which the system includes a no load tap changer on the primary winding to accommodate transmission system variations within a narrow band around the nominal rating.
This is a relatively recent development which uses thyristors both to switch the transformer winding taps and to pass the load current in the steady state.
IEC – IEC Tap changers. Part 2: Application guide
It commences operation at tap position 2, with load supplied directly via the right hand connection. This power consumption can add up to a few kilowatts which appears as heat and causes a reduction in overall efficiency 60214- the transformer; however, it results in a more compact design that reduces the size and weight of the tap changer device.
Please help to improve this article by introducing more precise citations. The disadvantage is that these tap changers are more complex and require a 602114-2 voltage power supply for the thyristor circuitry. This technique overcomes the problems with open or short circuit taps. It is important to us that you purchase the right document. In such systems, the tap changer will often be set just once, at the time of installation, although it may be changed later to accommodate a long-term change in the system voltage profile.
If you need help with the purchase or have any queries please email enquiries standards. In a resistance type tap changer, the changeover must be made rapidly to avoid overheating of the diverter. To reduce arcing at the contacts, the tap changer operates in a chamber filled lec insulating transformer oilor inside a vessel filled with pressurized SF 6 gas.
During a tap change operation, the potential rapidly increases between the two electrodes in the bottle, and some of the energy is dissipated in an arc discharge through the bottle instead of flashing across the diverter switch contacts.
From Wikipedia, the free encyclopedia. This prevents arcing on the main contacts and can lead to a longer service life between maintenance activities. All of the winding taps will then be routed into the tap changer compartment through a terminal array.
Safety of power transformers, power supply units and similar – Particular requirements – Particular requirements for isolating transformers and power supply units incorporating 602142 transformers You 602214-2 be interested in this related standard Safety of transformers, reactors, power supply units and similar products for supply voltages up to 1 V — Part 2.
Tap changers typically use numerous tap selector switches which may not be switched under load, broken into even and odd banks, and switch between the banks with a heavy-duty diverter switch which can switch between them under load. A mechanical tap changer physically makes the new connection before releasing the old using multiple tap selector switches but avoids creating high circulating currents by using a diverter switch to temporarily place a large diverter impedance in series with the short-circuited turns.
Assists in the selection of tap-changers designed in accordance with IEC for use in conjunction with the tapped windings of transformers or reactors. Alternatively, in some systems, the process of tap changing may be assisted by means of a rotary or slider switch.
This page was last edited on 15 Septemberat